Filter change alert system for an hvac system

ABSTRACT

Methods and systems for indicating a status of an air filter of an HVAC system may include receiving a measure that is related to an amount of flow restriction presented by the air filter in an HVAC system, using the measure to determine whether the air filter does not need replacing, the air filter needs to be replaced soon, or the air filter should be replaced now, and displaying on a display of an HVAC controller an air filter status indicator, wherein the air filter status indicator includes a stop-light metaphor. In one example, the air filter status indicator may display a green color when the air filter does not need replacing, display a yellow color when the air filter needs to be replaced soon, and display a red color when the air filter should be replaced now. In some cases, the air filter status indicator may also include a qualitative term indicative of the current status of the air filter.

TECHNICAL FIELD

This disclosure generally relates to HVAC systems that include an airfilter, and more particularly, to methods and systems for monitoring thecondition of the air filter and to provide an indication of when the airfilter should be changed.

BACKGROUND

Heating, ventilation, and/or air conditioning (HVAC) systems are oftenused to control the comfort level within a building or other structure.Such HVAC systems typically include an HVAC controller that controlsvarious HVAC components of the HVAC system in order to affect and/orcontrol one or more environmental conditions within the building. ManyHVAC systems, including many forced air HVAC systems, include an airfilter to help remove dust and other pollutants from within the buildingand to protect the HVAC equipment from dust buildup which may negativelyimpact system performance. The air filter will become dirty over time,and as part of regular maintenance, the air filter should be changed.Continuing to run an HVAC system with an excessively dirty filter canreduce the efficiency of the HVAC system, and in some cases, can causedamage and/or reduce the expected lifetime of some of the HVACcomponents.

SUMMARY

The present disclosure relates generally to methods and systems formonitoring the condition of an air filter of an HVAC system, and toprovide an indication of when the air filter should be changed. In oneillustrative example, a method is provided for indicating a status of anair filter on an HVAC controller that includes a display. Theillustrative method may include receiving a measure that is related toan amount of flow restriction presented by an air filter in an HVACsystem. The measure that is related to the amount of flow restrictionpresented by the air filter in the HVAC system may be used to determinewhether the air filter does not need replacing, the air filter needs tobe replaced soon, or the air filter should be replaced now. The methodmay then include displaying on the display of the HVAC controller an airfilter status indicator, wherein the air filter status indicatorincludes a stop-light metaphor. In one example, the air filter statusindicator may display a green color when the air filter does not needreplacing, display a yellow color when the air filter needs to bereplaced soon, and display a red color when the air filter should bereplaced now. In some cases, the air filter status indicator may alsoinclude a qualitative term indicative of the current status of the airfilter.

In some instances, it may be determined that the air filter does notneed replacing when the measure that is related to the amount of flowrestriction presented by the air filter in the HVAC system is below athreshold value. Also, it may be determined that the air filter needsreplacing soon when the measure that is related to the amount of flowrestriction presented by the air filter in the HVAC system has been ator above the threshold value for less than a predetermined amount oftime. Also, it may be determined that the air filter should be replacednow when the measure that is related to the amount of flow restrictionpresented by the air filter in the HVAC system has been at or above thethreshold value for more than the predetermined amount of time. These,however, are only examples.

HVAC controllers are also contemplated. One illustrative HVAC controllermay include a controller, a memory coupled to the controller, and adisplay coupled to the controller. The HVAC controller may be programmedto receive a measure that is related to an amount of flow restrictionpresented by the air filter in the HVAC system. This may include, forexample, a measure of current draw by a fan or blower of the HVAC systemthat drives air flow through the air filter, a measure of air flowthrough the air filter, and/or a measure of static pressure or adifferential pressure across the air filter. Then, using the measurethat is related to the amount of flow restriction presented by the airfilter in the HVAC system, the controller may determine whether the airfilter does not need replacing, the air filter needs to be replacedsoon, or the air filter should be replaced now. Then, the controller maydisplay on the display of the HVAC controller an air filter statusindicator, wherein the air filter status indicator includes a stop-lightmetaphor. In some cases, the air filter status indicator may display agreen color when the air filter does not need replacing, a yellow colorwhen the air filter needs to be replaced soon, and a red color when theair filter should be replaced now.

The preceding summary is provided to facilitate an understanding of someof the innovative features unique to the present disclosure and is notintended to be a full description. A full appreciation of the disclosurecan be gained by taking the entire specification, claims, drawings, andabstract as a whole.

BRIEF DESCRIPTION OF THE DRAWINGS

The disclosure may be more completely understood in consideration of thefollowing description of various embodiments in connection with theaccompanying drawings, in which:

FIG. 1 is a schematic view of an illustrative HVAC system located withina building or structure;

FIG. 2 is a schematic view of an illustrative HVAC controller;

FIG. 3 is a front view of an illustrative HVAC controller;

FIGS. 4-7 provide illustrative examples of various home screens that maybe displayed upon the HVAC controllers of FIGS. 2 and 3;

FIGS. 8-9 provide illustrative examples of various screens that may bedisplayed by an HVAC controller showing a status of one or morecomponents of the HVAC system;

FIG. 10 is a flow chart of an exemplary method of calibrating an HVACsystem filter monitor using a clean air filter;

FIGS. 11A-11I provide illustrative examples of different screens thatmay be displayed by an HVAC controller following exemplary methods ofcalibrating an HVAC system filter monitor;

FIG. 12 is a flow chart of an exemplary method of calibrating an HVACsystem filter monitor using a blocking panel;

FIG. 13A is a schematic view of an illustrative blocking panel used toat least partially block an air filter opening following the methodoutlined in FIG. 12;

FIG. 13B is a schematic view of an illustrative template used to size ablocking panel such as shown in FIG. 13A;

FIGS. 14A-14I provide illustrate examples of different screens that maybe displayed by an HVAC controller following the exemplary method ofcalibrating an HVAC system filter monitor outlined in FIG. 12;

FIG. 15 is a flow chart of an example method of determining a sensoroffset drift for an HVAC system filter monitor;

FIG. 16 is flow chart of an example method of monitoring a change in aphysical parameter across an air filter during operation of the HVACsystem;

FIGS. 17A-17E provide illustrative examples of different screens thatmay be displayed by an HVAC controller that is configured to display auser alert according to a user alert system; and

FIG. 18 is a flow chart of an example method of evaluating a new airfilter.

While the disclosure is amenable to various modifications andalternative forms, specifics thereof have been shown by way of examplein the drawings and will be described in detail. It should beunderstood, however, that the intention is not to limit aspects of thedisclosure to the particular embodiments described. On the contrary, theintention is to cover all modifications, equivalents, and alternativesfalling within the spirit and scope of the disclosure.

DESCRIPTION

The following description should be read with reference to the drawingswherein like reference numerals indicate like elements throughout theseveral views. The description and drawings show several embodimentswhich are meant to be illustrative of the claimed disclosure.

For convenience, the present disclosure may be described using relativeterms including, for example, left, right, top, bottom, front, back,upper, lower, up, and down, as well as others. It is to be understoodthat these terms are merely used for illustrative purposes and are notmeant to be limiting in any manner.

FIG. 1 is a schematic view of a building or other structure 2 having anillustrative heating, ventilation, and air conditioning (HVAC) system 4.While FIG. 1 shows a typical forced air type HVAC system, other types ofHVAC systems are contemplated including, but not limited to, boilersystems, radiant heating systems, electric heating systems, or any othersuitable type of HVAC system, as desired. The HVAC system 4 of FIG. 1includes one or more HVAC components 6, a system of ductwork and airvents including a supply air duct 10 and a return air duct 14, and oneor more HVAC controllers 18. The one or more HVAC components 6 mayinclude, but are not limited to, a furnace, a heat pump, an electricheat pump, a geothermal heat pump, an electric heating unit, an airconditioning unit, a humidifier, a dehumidifier, an air exchanger, anair cleaner, and/or the like.

It is contemplated that the HVAC controller(s) 18 may be configured tocontrol the comfort level in the building or structure by activating anddeactivating the HVAC component(s) 6. The HVAC controller(s) 18 may beconfigured to control the HVAC component(s) 6 via a wired or wirelesscommunication link 20. In some cases, the HVAC controller(s) 18 may be athermostat, such as, for example, a wall mountable thermostat, but thisis not required in all embodiments. In some embodiments, the one or moreHVAC controllers 18 may include multiple zone controllers, eachmonitoring and/or controlling the comfort level within a particular zonein the building or other structure. An illustrative HVAC controller,which is not meant to be limiting in any way, is disclosed in: USPublished Patent Application No. 20090140062, entitled “HVAC CONTROLLERTHAT SELECTIVELY REPLACES OPERATING INFORMATION ON A DISPLAY WITH SYSTEMSTATUS INFORMATION”; US Published Application No. 20090143880, entitled“HVAC CONTROLLER WITH CONTEXT SENSITIVE HELP SCREENS”; US PublishedApplication No. 20090143918, entitled “METHOD AND APPARATUS FORCONFIGURING AN HVAC CONTROLLER”; US Published Application No.20090143916, entitled “HVAC CONTROLLER HAVING A PARAMETER ADJUSTMENTELEMENT WITH A QUALITATIVE INDICATOR”; US Published Application No.20090143879, entitled “HVAC CONTROLLER WITH PARAMETER CLUSTERING”; USPublished Application No. 20090140056, entitled “HVAC CONTROLLER WITHQUICK SELECT FEATURE,” the entireties of which are incorporated hereinby reference for all purposes.

In the illustrative HVAC system shown in FIG. 1, the HVAC component(s) 6may provide heated air (and/or cooled air) via the ductwork throughoutthe building or other structure 2. As illustrated, the HVAC component(s)6 may be in fluid communication with every room and/or zone in thebuilding or other structure 2 via the ductwork 10 and 14. In operation,when a heat call signal is provided by the HVAC controller(s) 18, anHVAC component 6 (e.g., forced warm air furnace) may be activated tosupply heated air to one or more rooms and/or zones within the buildingor other structure 2 via supply air ducts 10. The heated air may beforced through supply air duct 10 by a blower or fan 22. In thisexample, the cooler air from each zone may be returned to the HVACcomponent 6 (e.g., forced warm air furnace) for heating via return airducts 14. Similarly, when a cool call signal is provided by the HVACcontroller(s) 18, an HVAC component 6 (e.g., air conditioning unit) maybe activated to supply cooled air to one or more rooms and/or zoneswithin the building or other structure via supply air ducts 10. Thecooled air may be forced through supply air duct 10 by the blower or fan22. In this example, the warmer air from each zone may be returned tothe HVAC component 6 (e.g., air conditioning unit) for cooling viareturn air ducts 14.

In some cases, the system of vents or ductwork 10 and/or 14 can includeone or more dampers 24 to regulate the flow of air. For example, one ormore dampers 24 may be coupled to one or more of the HVAC controllers 18and can be coordinated with the operation of one or more HVAC components6. The one or more HVAC controllers 18 may actuate dampers 24 to an openposition, a closed position, and/or a partially open position tomodulate the flow of air from the one or more HVAC components to anappropriate room and/or zone in the building or other structure. Thedampers 24 may be particularly useful in zoned HVAC systems, and may beused to control which zone(s) receives conditioned air from the HVACcomponents 6.

In many instances, one or more air filters 30 may be used to remove dustand other pollutants from the air inside the building or other structure2. In the illustrative example shown in FIG. 1, the air filter(s) 30 isinstalled in the return air duct 14 to filter the air prior to the airentering the HVAC component 6, but it is contemplated that any othersuitable location for the air filter(s) 30 may be used. The presence ofthe air filter(s) 30 may not only to improve the indoor air quality, butmay also may protect the HVAC components 6 from dust and otherparticulate matter that would otherwise be permitted to enter the HVACcomponent.

The air filter 30 may restrict the air flow within the HVAC system 4.The level of restriction may be characterized by, for example, adifferential pressure drop across the air filter 30, a static pressureon one or both sides of the air filter, an air flow through the airfilter, a current draw by the fan or blower 22 at a given fan speed,etc. The differential pressure drop across a new, clean air filter 30may be low, but may increase as the air filter 30 catches dust and otherparticulate matter during the operation of the HVAC system 4. After aperiod of time, the differential pressure drop across the air filter maybecome significantly higher and replacement of the air filter 30 may berequired to avoid potential damage to the HVAC system 4 and its variouscomponents.

The rate at which the air filter 30 may become dirty and needsreplacement is often dependent on a variety of factors, some of whichinclude the ductwork characteristics, equipment specifications, ageand/or condition of the HVAC component(s) 6, the duty cycle of the HVACcomponent(s) 6, the type of filter, elapsed time, among others. Oneapproach is to replace the air filter 30 on a regular basis (e.g. everythree months). However, this may lead to excessive cost due to morefrequent air filter replacement than needed, or may lead to a decreasein the efficiency and/or expected lifetime of the HVAC component(s) 6 inthe case of less frequent replacements than needed.

In some cases, and as shown in FIG. 1, the HVAC system 4 may include anair filter monitor 34. The air filter monitor 34 may be configured tomeasure or detect a change in a given parameter that is related to theamount of flow restriction presented by the air filter 30, such as astatic pressure or differential pressure drop across the air filter 30,an air flow through the air filter 30, the amount of current drawn bythe fan or blower 22 at a given fan speed, etc. In some cases, the airfilter monitor 34 may include a differential pressure sensor including afirst pressure tap 38 a located in the return (incoming) air duct 14 anda second pressure tap 38 b located in the supply (outgoing) air duct 10.In some cases, the pressure tap 38 a may be located outside the returnair duct 14 and may reference the ambient or atmospheric pressure. Insome cases, the air filter monitor 34 may include a flow sensor that iscapable of providing a measure that is related to the amount of air flowrestriction through the air filter 30. For example, the air filtermonitor 34 may be adapted to measure a flow rate, pressure, or acombination of flow rate and pressure through the air filter 30. Theseare just some examples.

The air filter monitor 34 may be configured to communicate with the HVACcontroller 18 via, for example, a wired or wireless communication link42. The air filter monitor 34 may communicate, relay or otherwisetransmit data regarding the selected parameter related to the amount offlow restriction presented by the air filter 30 to the HVAC controller18. The HVAC controller 18 may use the data from the air filter monitor34 to evaluate the filter status. In some cases, the HVAC controller 18may be configured to display information regarding the status of the airfilter 30 to a user, based on data received from the air filter monitor34. Also, and in some cases, the HVAC controller 18 may be configured toindicate to the user when a filter change may be necessary or desired.

FIG. 2 is a schematic view of an illustrative HVAC controller 18. Insome instances, HVAC controller 18 may be a thermostat, but this is notrequired. In the illustrative embodiment of FIG. 2, HVAC controller 18includes a controller/processor (e.g., microprocessor, microcontroller,etc.) 44 and a user interface 48. The processor 44 may be adapted tooperate in accordance with an algorithm that controls or at leastpartially controls one or more HVAC components 6 of an HVAC system suchas, for example, HVAC system 4 shown in FIG. 1. The processor 44 may,for example, operate in accordance with an algorithm that providestemperature set points, starting and/or ending times, and the like. Insome cases, HVAC controller 18 may include a timer (not shown). Thetimer may be integral to the processor 44 or may be provided as aseparate component.

In the illustrative embodiment, user interface 48 may be any suitableinterface that permits controller 18 to display and/or solicitinformation as well as permit a user to enter data such as temperatureset points, humidity set points, starting times, ending times, and thelike. In some cases, user interface 48 may include a display and adistinct keypad. A display may be any suitable display. In someinstances, a display may include or may be a liquid crystal display(LCD). If desired, user interface 48 may be a touch screen LCD panelthat functions as both display and keypad. In some instances, a touchscreen LCD panel may be adapted to solicit values for a number ofoperating parameters and/or to receive said values, but this is notrequired.

The illustrative HVAC controller 18 includes a memory block 52 that maybe considered as being electrically connected to processor 44. Memoryblock 52 may be used to store any desired information, such as theaforementioned control algorithm, set points, differential pressurelimits, and the like. Processor 44 may store information within memoryblock 52 and may subsequently retrieve the stored information. Memoryblock 52 may be any suitable type of storage device including, but notlimited to, RAM, ROM, EPROM, flash memory, a hard drive, and the like.

In some cases, as illustrated, HVAC controller 18 may include a dataport 56. Data port 56 may be configured to communicate with processor 44and may, if desired, be used to either upload information to processor44 or to download information from processor 44. Information that can beuploaded or downloaded may include values of operating parameters. Insome instances, data port 56 may be used to upload a previously-createdthermostat configuration into HVAC controller 18, thereby hastening theprogramming process. In some cases, data port 56 may be used to downloada thermostat configuration that has been created using HVAC controller18, so that the thermostat configuration may be used in otherthermostats. In some cases, data port 56 may be used to upload and/ordownload information pertaining to an HVAC dealer or contractor. In somecases, data port 56 may be a wireless port such as a Bluetooth™ port orany other wireless protocol. In other cases, data port 56 may be a wiredport such as a serial port, a parallel port, a CATS port, a USB(universal serial bus) port, or the like. In some instances, data port56 may be a USB port and may be used to download and/or uploadinformation from a USB flash drive. Other storage devices may also beemployed, as desired.

FIG. 3 is a front view of HVAC controller 18 according to anillustrative embodiment. As depicted in FIG. 3, HVAC controller 18 mayinclude a display 62 that is disposed within a housing 66. In somecases, display 62 may be a touch screen LCD display. If desired, display62 may be a dot matrix touch screen LCD display. A dot matrix touchscreen LCD display is a touch screen LCD that permits images such asletters, numbers, graphics, and the like to be displayed anywhere on theLCD, rather than being confined to predetermined locations such as isthe case with a fixed segment LCD. Housing 66 may be formed of anysuitable material, such as a polymeric material. In some cases, thehousing 66 may be formed such that it defines data port 56 (FIG. 2). Thehousing 66 may also include suitable wiring and/or other electricalconnections 68 such that the controller 18 may be electrically coupledto the building 2 and/or HVAC system 4.

In some cases, HVAC controller 18 may be configured to providesubstantial display and/or programming functionality, but this is notrequired. In some cases, HVAC controller 18 may be configured to displaya default display, also referred to herein as a home screen that isdisplayed by HVAC controller 18 when no other data entry is underway.FIG. 4 provides an example of a home screen 72 that may be displayed byHVAC controller 18. In some cases, home screens may include screens thatcan be accessed by a top level navigational menu. A home screen may, ifdesired, display one or more parameters relating to environmentalconditions such as indoor and/or outdoor temperature and/or humidity,expected weather conditions, and/or the status of any equipment that isat least partially controlled by HVAC controller 18.

As shown in FIG. 4, the display 62 may display an illustrative homescreen 72 that includes a navigational bar 76. Navigational bar 76 maybe considered as providing top level navigation, but this is notrequired. In some cases, if desired, navigational bar 76 may include oneor more of a HOME button 78, a FAN button 80, a SYSTEM button 82 and/ora MENU button 84. FIG. 4 is an example of a screen that may be displayedafter a user has pushed HOME button 78.

In some cases, home screen 72 may be considered as having two or moreregions. For example, home screen 72 may include a first region 86 and asecond region 88. In some instances, first region 86 may be consideredas displaying or otherwise providing primary information while secondregion 88 may be considered as displaying or otherwise providingsecondary information. In some cases, primary information may beinformation that is considered to be more important, more interestingand/or more useful than secondary information. To illustrate, firstregion 86 may display one or more of a current temperature reading, acurrent indoor humidity, a schedule status, and the like. Second region88 may display one or more of a date and time, an outdoor temperaturereading, an outdoor humidity reading, an equipment status, and the like.

Home screen 72 may also include a third region 90 that may be used fordisplaying and/or adjusting a parameter value such as a parameter thatis displayed within first region 86 of home screen 72. In some cases,for example, third region 90 may, as illustrated, display both a heatingtemperature set point and a cooling temperature set point, but this isnot required. Third region 90 may include a first parameter 92, a firstup arrow 94 and a first down arrow 96. Third region 90 may include asecond parameter 98, a second up arrow 100 and a second down arrow 102.First parameter 92 may be adjusted up or down using first up arrow 94and/or first down arrow 96, as appropriate. Second parameter 98 may beadjusted up or down using second up arrow 100 and/or second down arrow102, as desired.

In some cases, home screen 72 may be configured to display informationregarding the status of the air filter 30 (FIG. 1) of the HVAC system 4,and/or may be configured to indicate to a user when a filter change maybe necessary or desired. For example, in FIGS. 5 and 6, informationregarding the filter status may be displayed in the second region 88 ofthe home screen 72, but this is not required. In some cases, a filterstatus indicator 106 may be displayed in place of the informationpreviously displayed in that second region 88 or the filter statusindicator 106 may overlay the information that was previously displayedin the second region 88 of the home screen 72. In some cases, the filterstatus indicator 106 may be configured to display qualitative termsindicative of the current status of the air filter 30. As illustrated inFIG. 5, exemplary qualitative terms that may be used to indicate thestatus of the air filter may include, but are not limited to, “CLEAN”,“GOOD”, “DIRTY”, “CHANGE FILTER SOON”, “REPLACE FILTER SOON” “CHANGE AIRFILTER NEEDED”, “REPLACE AIR FILTER NOW” and “FILTER CHANGE REQUIRED”,among others. In other cases, as illustrated in FIG. 6, the filterstatus indicator 106 may be configured to display a graphicalrepresentation indicating the current status of the air filter 30. Forexample, a maximum number of bars displayed on a graph may representthat the status of the air filter 30 is good, while only a few barsdisplayed on a graph may indicate that a filter change is needed soon. Asingle bar or no bar at all displayed on a graph may represent that afilter change is need. In still other cases, as will be described inmore detail below, the filter status indicator 106 may be color coded ormay employ color-coded labels or indicators. In some cases, the filterstatus indicator 106 may be configured to produce an audible signal(e.g., intermittent beeps) that may indicate that a filter change isneeded or desired.

In some instances, information regarding the filter status may beaccessed by selecting the appropriate button, icon or tab provided, forexample, along the navigational bar 76. For example, as shown in FIG. 7,the user may access information regarding the filter status by selectingSTATUS button 108 provided along the navigational bar 76. Pressing theSTATUS button 108 may result in a status screen 112 being displayed onthe display 62 (FIG. 3). The status screen 112 may be configured todisplay information regarding the filter status.

In some cases, as illustrated in FIGS. 8 and 9, the status screen 112also may be configured to display information regarding other HVACsystem components. In some examples, the status screen 112 may include afirst region 116 and a second region 120. The first region 116 may beconfigured to display a table 124 that contains select informationregarding various system components of the HVAC system. Depending uponhow much information the table 124 is configured to contain, the table124 may be a scrollable table, but this is not required. In some cases,the table 124 may include at least one column and one row ofinformation. For example, different system components are listed in afirst column 128 labeled “EQUIPMENT.” The second column 132 labeled“SETTING” may provide the current setting for a select piece ofequipment listed in the first column 128. The third column 136 labeled“STATUS” may provide the current status for a select piece of equipmentlisted in the first column. The table 124 can be configured to contain adifferent number of columns and row containing information about theHVAC system as desired. The second region 120 may include a scroll baror sliding bar 140 that permits the user to move up and/or down withinthe table 124 to view select information regarding the system. Forexample, a system user may manipulate the sliding bar 140 up or downuntil information regarding the air filter is displayed.

In some cases, the table 124 may be configured to display qualitativeinformation regarding the air filter 30. The identifier or label “AIRFILTRATION” or “AIR FILTER” may appear in the table 124 in the firstcolumn 128 labeled “EQUIPMENT”. This may indicate to the user thatinformation pertaining to the air filter 30 appears in this row. Next,in the second column 132 labeled “SETTING”, information regarding thecurrent setting pertaining to the air filter 30 may be displayed.

In some cases, as shown in FIG. 8, the table 124 may be configured todisplay qualitative terms in the third column 136 indicative of thecurrent status of the air filter 30. Exemplary qualitative terms thatmay be used to indicate the status of the air filter include, but arenot limited to, “CLEAN”, “GOOD”, “DIRTY”, “CHANGE FILTER SOON”, “REPLACEFILTER SOON” “CHANGE FILTER NEEDED”, “REPLACE FILTER NOW” and “FILTERCHANGE REQUIRED”, among others. In other cases, as illustrated by theexample provided in FIG. 9, a graphical representation 144 indicatingthe current status of the air filter 30 may be displayed. For example, amaximum number of bars displayed on a graph may represent that the airfilter 30 is clean, while only a few bars displayed on a graph mayindicate that a filter change is needed soon. A single bar or no bar atall displayed on a graph may represent that a filter change is needed.In still other cases, color-coded labels or indicators may be used toindicate if a filter change is needed.

So that the HVAC controller 18 may display accurate informationregarding the status of the air filter 30, the air filter monitor 34 maybe calibrated. Calibrating the air filter monitor 34 may account forsystem variables/variations including, but not limited to, ductworkcharacteristics, equipment specifications, equipment set up, and thecondition of the equipment, among others. Additionally, calibration mayhelp ensure that the filter monitor 34 will work properly with theselected filter type and the particular HVAC system (e.g., HVAC system 4in FIG. 1). The filter monitor 34 may be capable of working with avariety of filter types and a variety of HVAC systems, as well asdifferent set-ups from different manufacturers. Calibration may also beused to provide a threshold value against which the parameter monitored(e.g., differential pressure drop across the air filter 30) may beevaluated.

FIG. 10 is a flow chart of an exemplary method 200 of setting an airfilter change threshold value for an HVAC system. In such a case, aclean air filter may be installed in the HVAC system and used todetermine and set an air filter change threshold value. The air filterchange threshold value may then be used to calibrate and indicate thestatus of the filter, and in some cases, as discussed in further detailbelow, may trigger an alert to the user that the air filter 30 is dirtyand may need to be replaced.

To determine and set an air filter change threshold value for the HVACsystem), first a system user (e.g., installer or HVAC contractor) mayinstall a clean air filter in the system. Next, in response to anindication that a clean air filter has been installed, the controllermay instruct the HVAC system to operate in a selected mode or state(Block 210). The HVAC system may be operated in a mode or state in whichthe fan is “on” and drives air through the air filter. In some cases,this may be a “fan only” mode or state in which the heating and/orcooling element is “off” and only the fan is operated at a selectedspeed. In other cases, the HVAC system may be operated in a heating mode(e.g., HEAT 1) or a cooling mode (e.g., COOL 2). In another case, theHVAC system may be operated in a ventilation mode. In still other cases,the HVAC system may be operated in a humidifying mode or dehumidifyingmode. Typically, the mode or state having the highest fan speed may beselected, but this is not always the case. In some cases, the mode maybe selected based on which mode or state may provide the greatestnegative impact on equipment life from a dirty filter.

While the HVAC system is operating in the selected mode, the controller(e.g., controller 18) may command or require the air filter monitor tomeasure the differential pressure across the clean air filter to obtaina system differential pressure measurement that is related to an amountof flow restriction presented by the clean air filter (Block 214). Thedifferential pressure measurement may then be displayed to the user bythe controller 18 on an appropriate screen of the display 62. In somecases the user may operate the HVAC system in various different states,obtaining a differential pressure or other measure related to an amountof flow restriction (e.g. air flow for a given fan speed) associatedwith the clean air filter for each state. However, each time a newmeasurement is obtained, it may replace the previous measurement, butthis is not required. When so provided, the differential pressuremeasurement (or other measure related to an amount of flow restriction)may be based on the last state in which the HVAC system is operated, butthis is not required.

Regardless of whether the user obtains a system differential pressuremeasurement from operating the HVAC system in a single or multiple modesor states, the system differential pressure measurement may be used todetermine an air filter change threshold value (Block 218). The airfilter change threshold value is indicative of an expected differentialpressure across what is considered a dirty filter. The air filter changethreshold value may be used to determine the status of the filter (e.g.,clean or dirty). In some cases, the user may use their own knowledge ofthe system variables that may affect the air filter change thresholdvalue for the specific application to determine or modify the air filterchange threshold value. Alternatively, or in addition, a processor 44may be programmed with an algorithm that may determine an air filterchange threshold value using a measure related to the amount of flowrestriction presented by the clean air filter. In some cases, thealgorithm may rely on only the differential pressure measurement, butthis is not required in all embodiments.

While not required, the algorithm used to determine the air filterchange threshold value may employ one or more inputs that may beprovided by the user. In some cases, the user may input informationregarding the HVAC system components in response to one or morequestions provided by the processor 44. For example, through the userinterface 48, the user may input information regarding the HVAC systemincluding, but not limited to, the MERV rating of the filter, the fantype (e.g., variable speed fan), the number of dampers, whether or notthe HVAC system is a zone system, the location of the HVAC components,the age of the components, and/or the size of the building or dwelling,among others. Using the data provided by the user and/or the system ameasure related to the amount of flow restriction presented by the cleanair filter (e.g. differential pressure measurement), the controller 18may calculate and sometimes subsequently display an air filter changethreshold value for the HVAC system.

In some cases, the air filter change threshold value may be set suchthat it is about 25%-400% higher than that measured for the clean airfilter. In some cases, the air filter change threshold value may be setsuch that it is about 5-300% higher than a differential pressuremeasurement associated with the clean air filter. In other cases, theair filter change threshold value may be set such that it is about5-200% higher than a differential pressure measurement associated withthe clean air filter. In other cases, the air filter change thresholdvalue may be set such that it is about 5-150% higher than a differentialpressure measurement associated with the clean air filter. In still yetother cases, the air filter change threshold value may be set such thatit is about 1-50% higher than a differential pressure measurementassociated with the clean air filter.

While the air filter change threshold value for indicating a dirtyfilter may be determined or adjusted by the user based on their ownknowledge and/or by the controller using an algorithm for that purpose,the air filter change threshold value may nonetheless be limited by anupper threshold value and/or a lower threshold value. For example, theindustry accepted standard for an air filter change threshold valueindicating a dirty air filter may be about 0.6 inches of water (w.c.).In some cases, the air filter change threshold value for indicating adirty filter determined by the user and/or the controller 18 may belimited to not exceed this or some other value. Similarly, the lowerthreshold value for the air filter change threshold value may be limitedto be no less than the system differential pressure measurement obtainedusing a clean air filter. For example, if the system differentialpressure measurement for a clean air filter is measured to be 0.1 w.c.,an exemplary range in which the air filter change threshold value forindicating a dirty filter may be confined to a range of 0.2 w.c. toabout 0.6 w.c., but this is not required.

In some instances, the air filter change threshold value may be storedin the memory 52 of the controller 18 (FIG. 2) (Block 222). In somecases, the processor 44 may be programmed with an algorithm that usesthe air filter change threshold value stored in the memory 52 todetermine the status of the air filter 30 by comparing, for example, acurrent differential pressure measurement to the air filter changethreshold value, and based on the results of this comparison, maytrigger an alert indicating that that the air filter is dirty and needsto be replaced.

In some cases, setting an air filter change threshold value using aclean air filter may be initiated by a user through the user interface48 of the controller 18. FIGS. 11A-11H provide several illustrativeexamples of various display screens 230, 232, 234, 236, 238, 240, 242,and 244 that may be displayed by the controller 18 while setting an airfilter change threshold value using a clean air filter.

To initiate the protocol for setting an air filter change thresholdvalue, the user may first select the MENU button 248 displayed on thedisplay screen 230 of the controller 18 (FIG. 11A). In response, a menuscreen 232 may be displayed (FIG. 11B). The menu screen 232 may beconfigured to display a menu 250 listing at least one menu option 252.The menu 250 may display multiple menu options 252 in the form of atable 254. The table 254 may be a scrollable table in which case, ascroll bar 256 may also be provided to enable to the user to navigate upand/or down within the table 254 to view the different menu options 252.Exemplary menu options 252 may include a security settings menu option,a dealer information option, and/or installer options menu option.

In some cases, the calibration protocol may be accessed by selected themenu option 252 labeled INSTALLER OPTIONS. Selection of the INSTALLEROPTIONS menu option 252 may cause the controller 18 to display anINSTALLER OPTIONS menu screen 234 (FIG. 11C). The INSTALLER OPTIONS menuscreen 234 may be configured to display one or more menu options 258listing at least one installer option accessible via the INSTALLEROPTIONS menu screen 234. The menu options 258 may be provided in theform of a table 262. The table 262 may be a scrollable table in whichcase, a scroll bar 266 may be provided to enable the user to navigate upand/or down within the table 262 to view the different installer optionsavailable to the user. Exemplary installer options available to the usermay include, but are not limited to, CREATE SETUP, VIEW/EDIT CURRENTSETUP, FILTER MONITORING CALIBRATION, and SET DIAGNOSTIC LIMITS, amongothers. The INSTALLER OPTIONS menu screen 234 may also be configured todisplay a PREVIOUS MENU button 270 that, upon its selection, may beprogrammed to return the user to the previous display screen, and a HELPbutton 272 that upon its selection may be configured to display a HELPmenu listing various help topics to the user.

The protocol for setting an air filter change threshold value may beinitiated by selecting the button 258 labeled FILTER MONITORINGCALIBRATION on the INSTALLER OPTIONS menu screen 234. Selecting theFILTER MONITORING CALIBRATION button 258 on the INSTALLER OPTIONS menuscreen 234 may cause a CALIBRATION menu screen 236 to be displayed (FIG.11D). The CALIBRATION menu screen 236 may display one or more buttons276 a, 276 b labeled with the different filter calibration methods thatmay be employed by the user to determine and set an air filter changethreshold value. For example, as shown in FIG. 11D, the CALIBRATION menuscreen 236 may be configured to display a first button 276 a labeledCLEAN FILTER CALIBRATION and a second button 276 b labeled BLOCKEDFILTER CALIBRATION. In some cases, the CALIBRATION menu screen 236 maybe configured to display a user prompt 278 that may prompt the user toselect a calibration method from the different calibration methodoptions that may be displayed by the CALIBRATION menu screen 236. TheCALIBRATION menu screen 236 may be also configured to display a HELPbutton 280 and/or a CANCEL button 282 which, if selected, may return theuser to the previous INSTALLER OPTIONS menu screen 234. Selection of thecalibration method may be initiated by pressing either the CLEAN FILTERCALIBRATION button 276 a or the BLOCKED FILTER CALIBRATION button 276 b.In this example, as shown in FIG. 11D, the CLEAN FILTER CALIBRATIONMETHOD button 276 a is highlighted indicating to the user that the CLEANFILTER METHOD option has been selected. Selection of the CLEAN FILTERCALIBRATION METHOD may be confirmed and/or initiated by pressing theNEXT button 286 displayed on the CALIBRATION menu screen 236.

Selection of the calibration method (e.g., the CLEAN FILTER CALIBRATIONmethod), may cause a first user prompt screen 237 to be displayed (FIG.11E). Here, in this example, upon selection of the CLEAN FILTERCALIBRATION method on the previous CALIBRATION menu screen 236, a firstuser prompt screen 237 may be displayed including a user prompt 287prompting the user to select a mode in which to operate the HVAC systemduring the selected calibration method from at least two differentoperation mode options 289 a, 289 b, and 289 c that may be displayed bythe first user prompt screen 287. For example, as shown in FIG. 11E, theuser may select from a Heat Stage 1 mode, a Heat Stage 1 and 2 mode, ora Cool Stage 1 mode. The operation mode for calibration may be selectedbased on the mode that may provide the greatest negative impact onequipment life.

Selection of the desired mode may be initiated by pressing the button oricon 289 a, 289 b or 289 c associated with the desired mode ofoperation. In this example, as shown in FIG. 11E, button 289 bassociated with Heat Stage 1 and 2 is highlighted indicating to the userthat this is the selected mode in which the HVAC system will operateduring the selected calibration method. Selection of the desired modemay be confirmed and/or initiated by pressing the NEXT button 286displayed on the first user prompt screen 287. A button or icon 291labeled BACK or RETEST may be displayed by the first user prompt screen237 and may permit a user to return to this screen 237 or a previousscreen when executing the selected calibration method in multiple modes.

After the mode in which to operate the HVAC system during the desiredcalibration method has been selected and confirmed, a second user promptscreen 238 may be displayed (FIG. 11F). Here, in this example, uponselection of the Heat Stage 1 and 2 mode on the previous user promptscreen 237, a second user prompt screen 238 may be displayed including auser prompt 288, prompting the user to install a clean air filter intothe HVAC system. The user prompt 288 may also provide certaininstructions to the user. In this example, as shown in FIG. 11F, theuser prompt 288 may also instruct the user to press a button 292 labeled“Calibrate for Clean Filter Now” which may also appear on the first userprompt screen 238. Selecting the “Calibrate for Clean Filter Now” mayfinalize initiation of the calibration protocol and may cause thecontroller 18 to initiate a calibration protocol. The user prompt screen238 may also be configured to display a BACK button 294 which may returnthe user to a previous screen (e.g., screen 236), a HELP button 296which upon its selection may cause a HELP menu to be displayed, and/or aCANCEL button 298, which may cancel the selection of the desiredcalibration method (e.g., CLEAN FILTER CALIBRATION) and which may returnthe user to the previous screen (e.g., CALIBRATION menus screen 236) ora home screen.

Upon initiation of the selected calibration method, the display may beconfigured to display a STATUS screen 240 (FIG. 11G). The STATUS screen240 may be configured to display a message 302 to the user indicatingthe current status of the calibration. The STATUS screen 240 may alsoindicate to the user that the controller 18 is busy.

Upon initiation of the clean air filter calibration method, thecontroller 18 may be configured to instruct or command the air filtermonitor 34 to measure, for example, a differential pressure, across theclean air filter 30 installed by the user in response to the selectionof the appropriate calibration method displayed by the first user promptscreen 238. Rather than a differential pressure measurement, it iscontemplated that a static pressure measurement, an air flowmeasurement, or any other suitable measurement that is related to anamount of flow restriction presented by the air filter may be used. Insome cases, after a measurement is made with the clean air filter, thecontroller 18 may be configured to display the measured value (e.g.differential pressure measurement value) on a third user prompt screen242 (FIG. 11H). The third user prompt screen 242 may include multipleregions for conveying a variety of information to the user. For example,the third user prompt screen 242 may display a differential pressuremeasurement value obtained during calibration in a first region 306, anda user prompt 308 in a second region 310. The third user prompt screen242 may be configured to display the selected calibration method in thefirst region 306 adjacent the differential pressure measurement value.The user prompt 308 may instruct or prompt the user to set or adjust anair filter change threshold value which may indicate a dirty filterbased on, for example, the differential pressure measurement displayedin the first region 306. In some cases, the controller may automaticallyprovide a default air filter change threshold value by, for example,adding an offset to the differential pressure measurement value.

In some cases, an adjustment bar 312 for adjusting or setting the airfilter change threshold value may be provided in a third region 314 ofthe third user prompt screen 242 situated below the second region 310containing the user prompt 308 and adjacent to the first region 306displaying the differential pressure measurement value obtained duringcalibration. The adjustment bar 312 may be either a horizontaladjustment bar as depicted in FIG. 11H or may be a vertical adjustmentbar. The adjustment bar 312 may include a slider 318 adapted to displaya label 320 indicating a current quantitative setting of the air filterchange threshold value. Additionally, the adjustment bar 312 may includea first button 322 and a second button 324 for increasing and decreasingthe setting for the air filter change threshold value. In some cases, asthe user increases and/or decreases the air filter change thresholdvalue displayed by the controller using the first and/or second button322, 324, the label 320 may indicate the current setting of the airfilter change threshold value, and may continuously or incrementallychange the value as it is increased or decreased. In some cases, thethird user prompt screen 242 may also include at least one of a RETESTbutton 326, a HELP button 328, a CANCEL button 330, and a DONE button332 located in a fourth region 334 of the display screen 242. Uponselection of the RETEST button 326, the controller 18 may be configuredto re-execute the selected calibration method (e.g., clean filtercalibration). The user may select the RETEST button 326 if they aredissatisfied with or question the differential pressure (or other)measurement that was obtained during the calibration that was justconducted. Selecting the HELP button 328 may cause a HELP menu to bedisplayed. Selecting of the CANCEL button 330 may cancel the currentoperation (e.g., adjustment of the threshold value) and may return theuser to a previous screen (e.g., CALIBRATION menu screen 236) or a homescreen (e.g., Home Screen 230).

After setting the air filter change threshold value, the user may selectthe DONE button 332 to indicate that that the air filter changethreshold value has been set. This may cause the controller 18 to storethe air filter change threshold value in its memory for reference duringoperation of the HVAC system. Additionally, this is the value upon whichthe controller 18 may use to determine the status of the air filterduring subsequent operation of the HVAC system, and which may be used totrigger an alert to the user indicative of the status of the air filter.

Additionally, selection of the DONE button 332 may cause a confirmationscreen 244 to be displayed (FIG. 11I). The confirmation screen 244 mayinclude one or more user messages 336 that may indicate to the user thatthe threshold value has been set. The confirmation screen 244 may alsobe configured to display an OK button 338 prompting the user toacknowledge the message displayed by the confirmation screen 244. Uponselecting the OK button 338, the INSTALLER OPTIONS menu screen 234 (FIG.11C) or the HOME screen 230 (FIG. 11A) may be displayed.

The air filter change threshold value also may be set using a blockedair filter (and/or blocking panel). When so provided, an at leastpartially blocked air filter (and/or blocking panel) may be used todetermine and set an air filter change threshold value. Like above, theair filter change threshold value may then be used to indicate thestatus of the filter, and in some cases, may trigger an alert to theuser that the air filter 30 is dirty and may need to be replaced.

FIG. 12 is a flow chart of a method 350 in which an at least partiallyblocked air filter (and/or blocking panel) is used to determine and setan air filter change threshold value for an HVAC system. An at leastpartially blocked air filter (and/or blocking panel) may be used in thismethod to simulate a dirty air filter, and in some cases, may provide amore accurate assessment of the performance of the HVAC system when theair filter is considered dirty.

To determine and set an air filter change threshold value for an HVACsystem using an at least partially blocked air filter (and/or blockingpanel), a system user (e.g., installer or HVAC contractor) may install aclean air filter in the system (Block 354). Next, the user may install ablocking panel into the system to at least partially block the clean airfilter to simulate a dirty air filter (Block 354). The blocking panelmay be a piece of cardboard, cardstock, poster board, or similarmaterials that may be inserted into the system to at least partiallyblock the air filter in order to simulate a dirty air filter. Theblocking panel may be installed in the system such that it at leastpartially blocks the return air side or the supply air side of thefilter. The blocking panel may be sized using a template for thatpurpose. The template may be provided with the installation guide forthe air filter monitor. In some cases, the blocking panel may also beprovided with an installation guide. In some cases, a blocking panel maybe used without a clean air filter installed. That is, the blockingpanel may replace the air filter in the HVAC system, at leasttemporarily during calibration.

In some cases, a kit for installing an air filter monitor may include aninstallation guide or manual including instructions for installing andcalibrating the air filter monitor. The kit may also include a templatefor sizing a blocking panel to achieve a desired reduction in air flow(% air flow blockage) in the HVAC system. In certain cases, a blockingpanel may be initially provided with the kit. The template and theblocking panel may be discarded after successful installation andcalibration of the air filter monitor.

FIGS. 13A and 13B are schematic diagrams of a blocking panel 378 andtemplate 382 that may be used to size the blocking panel 378,respectively. In some cases the template 382 may be a part of andprinted on the blocking panel 378. In other cases, the template 382 maybe provided separately from the blocking panel. The template 382 may beused to size the blocking panel such that when the blocking panel 378 isinserted into the HVAC system, it results in at least a 25% air flowblockage, at least a 33% air flow blockage, at least a 50% air flowblockage, at least a 67% air flow blockage, or at least a 75% blockage.These are just some examples. The amount of blockage used to simulate adirty filter may be selected by the user. In some cases, a 50% air flowblockage may be used.

In some cases, as shown in FIG. 13B, the template 382 may be a piece ofpaper or thin cardstock including at least one set of horizontal andvertical measurement lines 386 a-386 e that may be used to size theblocking panel 378 such that it results in a desired amount of air flowblockage. The template 382 may also include one or more labels 390 forindicating to the user the approximate percent air flow blockage thatmay result when a particular set of measurement lines 386 a-386 e areused to size the blocking panel 378. For example, as shown in FIG. 13B,the template 382 may include a first set of measurement lines 386 a thatwhen used to size the blocking panel 378, may result in about a 25% airflow blockage. In some cases, the template 382 may include additionalsets of measurement lines 386 b-386 e that when used to size a blockingpanel, may result in at least a 33% air flow blockage, at least a 50%air flow blockage, at least a 67% air flow blockage, or at least a 75%blockage, respectively. In some cases, different sets of lines may beprovided on the template, where each set of lines corresponds to acorresponding size air filter. This way, one blocking panel and templatemay be suitable for calibrating HVAC systems with different size airfilters and/or different air flow blockages, as desired. In some cases,the blocking panel 378 may be sized by placing the template on theblocking panel 378 and using a cutting tool such as, for example, a pairof scissors, a razor blade, or an X-ACTO® knife to cut along theselected set of measurement lines 386 a-386 e.

Referring again to FIG. 12, after the blocking panel has been sized toachieve the desired amount of air flow blockage and inserted into thesystem, the user may select a system mode or state in which to operatethe HVAC system (Block 362). The HVAC system may be operated in a modeor state in which the fan is “on” and drives air through the blockingpanel and/or air filter. In some cases, this may be a “fan only” stateor mode in which the heating and/or cooling element is “off” and onlythe fan is operated at a selected speed. In other cases, the HVAC systemmay be operated in a heating mode (e.g., HEAT 1) or a cooling mode(e.g., COOL 2). In another cases, the HVAC system may be operated in aventilation mode. In still other cases, the HVAC system may be operatedin a humidifying mode or a dehumidifying mode. Typically, the modehaving the highest fan speed is selected, but this is not always thecase. In some cases, the mode may be selected based on which mode mayprovide the greatest negative impact on equipment life from a dirtyfilter. The HVAC system may then be operated in the selected mode withthe blocking panel to obtain, for example, a differential pressure orother measure related to an amount of flow restriction presented by theblocking panel (Blocks 358 and 362). In some cases, the user may operatethe HVAC system in various different modes, obtaining a differentialpressure or other measure related to an amount of flow restrictionpresented by the blocking panel for each mode. In some cases, each timea new measurement is obtained it may replace the previous measurement.Thus, the system differential pressure measurement associated with theat least partially blocked air filter may be based on the last mode inwhich the HVAC system is operated, but this is not required.

In some cases, after the system differential pressure measurement (orother measure related to an amount of flow restriction presented by theblocking panel) is obtained, the user may verify that the change in airtemperature across the heat exchanger and the discharge air temperatureare within an acceptable range suitable for the particular system (Block370). This verification may be accomplished in any suitable way. Forexample, and in a first method, a return air sensor and a discharge airsensor may be connected to the HVAC controller 18. The HVAC system maythen be configured to display the change in air temperature across theheat exchanger. In a second illustrative method, a discharge air sensormay be connected to the HVAC system controller and the HVAC systemcontroller may be configured to display the discharge air temperature.The user may then measure the change in air temperature across the heatexchanger using standard HVAC air temperature measurement tools. In athird illustrative method, neither a return air temperature nor adischarge air temperature is utilized. Instead, the user may simplymeasure the change in air temperature across the heat exchanger and thedischarge air temperature using standard HVAC air temperaturemeasurement tools. These are merely illustrative.

If the change in temperature across the heat exchanger and/or thedischarge air temperature are not within acceptable limits, then theuser may adjust the amount of blockage by re-sizing the blocking panelor by using a different blocking panel, and may repeat the stepsoutlined in Blocks 362, 366, and 370. If the change in temperatureacross the heat exchanger and/or the discharge air temperature are foundto be within the acceptable limits, the user may repeat the stepsoutlined in Blocks 362, 366, and 370 for multiple system modes, ifdesired. In some cases, the differential pressure measurement (or othermeasure related to an amount of flow restriction presented by theblocking panel) that is obtained may be based on the last mode in whichthe system was operated.

In some cases, the differential pressure measurement (or other measurerelated to an amount of flow restriction presented by the blockingpanel) may be displayed to the user by the controller 18. It iscontemplated that the system differential pressure measurement (or othermeasure related to an amount of flow restriction presented by theblocking panel) may be used, at least in part, to determine an airfilter change threshold value (Block 366). Subsequently, the air filterchange threshold value may be used to determine the status of the filter(e.g., clean or dirty). In some cases, the user may use their knowledgeof the system variables that may affect the differential pressurethreshold value for the specific HVAC system to determine or alter theair filter change threshold value, but this is not required.

In many cases, the air filter change threshold value may be set suchthat it is substantially equal to the measure that is related to theamount of air flow restriction presented by the at least partiallyblocked air filter. In this instance, the user may accept the measure asthe default air filter change threshold value.

While the air filter change threshold value for indicating a dirtyfilter may be adjusted by the user based on their knowledge or by thecontroller using an algorithm for that purpose, the air filter changethreshold value may be limited by an upper threshold value and a lowerthreshold value, as described above.

The air filter change threshold value may be stored in the memory 52 ofthe controller 18 (Block 370). In some cases, the processor 44 may beprogrammed with an algorithm that uses the air filter change thresholdvalue stored in the memory 52 to determine the status of the air filterby comparing a current measure related to an amount of flow restrictionpresented by the air filter to the air filter change threshold value,and that, based on the results of this comparison, may trigger an alertindicating that that the filter is dirty and needs to be replaced. Afterthe air filter change threshold value is set, the blocking panel may beremoved from the HVAC system (Block 376).

The protocol for setting an air filter change threshold value using anat least partially blocked air filter may be initiated by a user throughthe user interface 48 of the controller 18 (FIGS. 1 and 2). FIGS.14A-14G provide examples of various illustrative display screens 402,406, 410, 414, 418, 422, and 426 that may be displayed by the controller18 while setting an air filter change threshold value using an at leastpartially blocked air filter following a method such as, for example,described above with reference to FIG. 12.

To initiate the protocol for setting an air filter change thresholdvalue using an at least partially blocked air filter (and/or blockingpanel), the user may first select the MENU button 430 displayed on thedisplay screen 402 of the controller (FIG. 14A). In response, a menuscreen 406 may be displayed (FIG. 14B). The menu screen 406 may beconfigured to display a menu 434 listing at least one menu option 438.The menu 434 may display multiple menu options 438 in the form of atable 442. The table 434 may be a scrollable table in which case, ascroll bar 446 may also be provided to enable to the user to navigate upand/or down within the table 442 to view the different menu options 438.Exemplary menu options 438 may include a SECURITY SETTINGS menu option,a DEALER INFORMATION menu option, and/or INSTALLER OPTIONS menu option.

In some cases, the protocol for setting the air filter change thresholdvalue may be accessed by selected the menu option 438 labeled INSTALLEROPTIONS. Selection of the INSTALLER OPTIONS menu option 438 may causethe controller to display an INSTALLER OPTIONS menu screen 410 (FIG.14C). The INSTALLER OPTIONS menu screen 410 may be configured to displayone or more menu options 450 listing at least one installer optionaccessible via the INSTALLER OPTIONS menu screen 410. The menu options450 may be provided in the form of a table 454. The table 454 may be ascrollable table in which case, a scroll bar 458 may be provided toenable the user to navigate up and/or down within the table 454 to viewthe different installer options available to the user. Exemplaryinstaller options available to the user may include, but are not limitedto, CREATE SETUP, VIEW/EDIT CURRENT SETUP, FILTER MONITORINGCALIBRATION, and SET DIAGNOSTIC LIMITS, among others. The INSTALLEROPTIONS menu screen 410 may also be configured to display a PREVIOUSMENU button 462 that upon its selection, may be programmed to return theuser to the previous display screen or home screen 402, and a HELPbutton 464 that upon its selection may be configured to display a HELPmenu listing various help topics to the user.

The protocol for setting the air filter change threshold value may beinitiated by selecting the button 450 labeled FILTER MONITORINGCALIBRATION on the INSTALLER OPTIONS menu screen 410. Selecting theFILTER MONITORING CALIBRATION button 450 on the INSTALLER OPTIONS menuscreen 410 may cause a CALIBRATION menu screen 414 to be displayed (FIG.14D). The CALIBRATION menu screen 414 may display one or more buttons466 a, 466 b labeled with the different filter calibration methods thatmay be employed by the user to determine and set the air filter changethreshold value. For example, as shown in FIG. 14D, the CALIBRATION menuscreen 414 may be configured to display a first button 466 a labeledCLEAN FILTER CALIBRATION and a second button 466 b labeled BLOCKEDFILTER CALIBRATION. In some cases, the CALIBRATION menu screen 414 maybe configured to display a user prompt 470 that may prompt the user toselect a calibration method from the different calibration methodoptions that may be displayed by the CALIBRATION menu screen 414. TheCALIBRATION menu screen 414 may be also configured to display a HELPbutton 474 and/or a CANCEL button 478 which, if selected, may return theuser to the previous INSTALLER OPTIONS menu screen 410 or home screen402. Selection of the calibration method may be initiated by pressingeither the CLEAN FILTER CALIBRATION button 466 a or the BLOCKED FILTERCALIBRATION button 466 b. In this example, as shown in FIG. 11D, theBLOCKED FILTER CALIBRATION METHOD button 466 b is highlighted indicatingto the user that the BLOCKED FILTER METHOD option has been selected.Selection of the BLOCKED FILTER CALIBRATION METHOD may be confirmedand/or initiated by pressing the NEXT button 482 displayed on theCALIBRATION menu screen 414.

Selection of the calibration method (e.g., the BLOCKED FILTERCALIBRATION method), may cause a user prompt screen 416 to be displayed(FIG. 11E). Here, in this example, upon selection of the BLOCKED FILTERCALIBRATION method on the previous CALIBRATION menu screen 414, a userprompt screen 416 may be displayed including a user prompt 483 promptingthe user to select a mode in which to operate the HVAC system during theselected calibration method from at least two different operation modeoptions 484 a, 484 b, and 484 c that may be displayed by the user promptscreen 416. For example, as shown in FIG. 11E, the user may select froma Heat Stage 1 mode, a Heat Stage 1 and 2 mode, or a Cool Stage 1 mode.The operation mode for calibration may be selected based on the modethat may provide the greatest negative impact on equipment life.

Selection of the desired mode may be initiated by pressing the button oricon 484 a, 484 b or 484 c associated with the desired mode ofoperation. In this example, as shown in FIG. 11E, button 484 bassociated with Heat Stage 1 and 2 is highlighted indicating to the userthat this is the selected mode in which the HVAC system will operateduring the selected calibration method. Selection of the desired modemay be confirmed and/or initiated by pressing the NEXT button 485displayed on the user prompt screen 416.

After the mode in which to operate the HVAC system during the desiredcalibration method has been selected and confirmed, the controller 18may be configured to measure a discharge air temperature and/or a changein air temperature across the heat exchanger to verify that these valuesare still within an acceptable range for the HVAC system when an atleast partially blocked air filter is installed within the system.Additionally, the controller 18 may subsequently be configured todisplay a discharge air temperature verification screen 417 displayingthe discharge air temperature and or change in air temperature acrossthe heat exchanger in a first region 491 of the screen 417 (FIG. 11F).The screen 417 may include a user prompt 492 prompting the user toverify that the displayed discharge air temperature and/or change in airtemperature is within an acceptable range for the HVAC system beforefinal initiation of the BLOCKED FILTER CALIBRATION method. The BLOCKEDFILTER CALIBRATION method may be initiated by selecting a button 493labeled CALIBRATE FOR BLOCKED FILTER NOW provided on the discharge airtemperature verification screen 417.

Upon initiation of the selected BLOCKED FILTER CALIBRATION method, thecontroller may be configured to display a STATUS screen 418 (FIG. 14G).The STATUS screen 418 may be configured to display a message 486 to theuser indicating the current status of the calibration. The STATUS screen418 may also indicate to the user that the controller is busy.

Upon initiation of the blocked filter calibration method, the controller18 may be configured to measure, for example, a differential pressurevia the air filter monitor 34 across the at least partially blocked airfilter (and/or blocking panel) to obtain a measurement related to anamount of air flow restriction presented by the blocking panel. After adifferential pressure measurement has been obtained by the controller,the controller 18 may be configured to display the differential pressuremeasurement value obtained during the blocked air filter calibration ona CALIBRATION RESULTS screen 422 (FIG. 14H). The CALIBRATION RESULTSscreen 422 may include multiple regions for conveying a variety ofinformation to the user. For example, the CALIBRATION RESULTS screen 422may display the differential pressure measurement value obtained duringcalibration in a first region 490 and a user message 494 in a secondregion 498. The CALIBRATION RESULTS screen 422 may also be configured todisplay the calibration method in the first region 490 adjacent thedifferential pressure measurement value. The user message 494 mayinstruct or prompt the user to set or adjust an air filter changethreshold value which may indicate a dirty filter based on thedifferential pressure measurement displayed in the first region 490.

An adjustment bar 502 for adjusting or setting the air filter changethreshold value may be provided in a third region 506 of the screen 422situated below the second region 498 containing the user message 494 andadjacent to the first region 490 displaying the differential pressuremeasurement value obtained during calibration. The adjustment bar 502may be either a horizontal adjustment bar as depicted in FIG. 14H or maybe a vertical adjustment bar. The adjustment bar 502 may include aslider 510 adapted to display a label 514 indicating a current settingof the differential pressure threshold value. Additionally, theadjustment bar 502 may include a first button 518 and a second button522 for increasing and decreasing the setting for the differentialpressure threshold value. In some cases, as the user increases and/ordecreases the air filter change threshold value using the first and/orsecond button 518, 522 the label 514 indicating the current setting ofthe air filter change threshold value may also continuously orincrementally change to indicate the current setting of the air filterchange threshold value as it is increased or decreased. In some cases,one or more qualitative labels 526 may be provided over the adjustmentbar indicating in which direction the slider 510 may be moved indicatinga clean or dirty filter. Exemplary qualitative labels include the termsCLEAN, DIRTY, CLEANER, DIRTIER, GOOD, BAD, OK, REPLACE, and REPLACESOON, among others. Similarly, the buttons 518, 522 may also includedirectional arrows indicating in which direction the slider 510 may bemoved to indicate a clean or dirty filter.

The CALIBRATION RESULTS screen 422 may also include at least one of aRETEST button 530, a HELP button 532, a CANCEL button 534, and a DONEbutton 538 located in a fourth region 542 of the display screen 422.Upon selection of the RETEST button 530, the controller may beconfigured to re-execute the selected calibration method (e.g., BLOCKEDFILTER CALIBRATION). The user may select the RETEST button 530 if theyare dissatisfied with or question the differential pressure measurementthat was obtained by calibration that was just conducted. Selecting theHELP button 532 may cause a HELP menu to be displayed. Selecting of theCANCEL button 534 may cancel the current operation (e.g., adjustment ofthe threshold value) and may return the user to a previous screen (e.g.,CALIBRATION menu screen 414) or a home screen (e.g., HOME screen 402).

In the example shown, the user may choose to either accept thedifferential pressure measurement as the default air filter changethreshold value or may choose to adjust the differential measurementvalue to set the air filter change threshold value. After setting theair filter change threshold value, the user may select the DONE button538 to indicate that that the air filter change threshold value has beenselected. This may cause the controller to store the air filter changethreshold value in its memory for reference during operation of the HVACsystem. Additionally, this is the value upon which the controller 18 mayuse to determine whether or not an air filter is clear or dirty, andwhich may be used to trigger an alert to the user that may indicate thatthe filter needs to be replaced.

Additionally, selection of the DONE button 538 may cause a CONFIRMATIONscreen 426 to be displayed (FIG. 14I). The CONFIRMATION screen 426 mayinclude one or more user messages 546 that may indicate to the user thatthe threshold value has been adjusted. The CONFIRMATION screen 426 mayalso be configured to display an OK button 552 prompting the user toacknowledge the message displayed by the confirmation screen 426. Uponselecting the OK button 552, the INSTALLER OPTIONS screen 410 (FIG. 14C)or the HOME screen 402 (FIG. 14A) may be displayed.

Referring again to FIG. 1, the air filter monitor 34 may be used tomonitor the air filter 30 during operation of the HVAC system 4. For thepurposes of this discussion, the air filter monitor 34 will be describedas being adapted to measure a differential pressure across the airfilter 30 between the supply air side and the return air side of the airfilter 30. However, it must be understood, that the air filter monitor34 may be adapted to measure a different physical parameter or to detecta change in a different physical parameter, such as air flow through theair filter, a static pressure on one or both sides of the air filter,current draw by the fan or blower 22 at a given fan speed, etc., aspreviously discussed.

In many cases, the air filter monitor 34, as described herein, mayinclude a differential pressure sensor, which may experience a sensoroffset and/or sensor drift over time and with temperature and/or overother environmental conditions. Sensor offset and/or sensor offset driftmay decrease the accuracy of the differential pressure measurement. Toimprove accuracy of the differential pressure measured by the air filtermonitor 34, sensor offset and/or sensor drift may be taken into account.

To determine sensor offset and/or sensor offset drift over time, thedifferential pressure between an upstream side and a downstream side ofthe air filter 30 may be measured at or near zero system pressure (e.g.with substantially no air flowing through the air filter). Whiledifferential pressure is used here as an example, it is contemplatedthat offsets for other sensors may be removed in a similar manner. Itshould be generally recognized that it is possible that a minimal amountof pressure may be present in the system, but that this minimal pressuremay be considered to be negligible. In an ideal system, the differentialpressure between the upstream side and the downstream side of the airfilter 30 at zero system pressure should be equal to zero. However, thisis not always the case for a variety of reasons. As such, thedifferential pressure measurement at zero pressure may be indicative ofa sensor offset, which may drift with time and may reduce the accuracyof the differential pressure value. As such, and to improve the accuracyof the system, it is contemplated that the sensor offset may be measuredfrom time to time and eliminated when determining the status of the airfilter 30.

FIG. 15 outlines a method 600 of monitoring a status of an air filter(e.g., air filter 30) using a sensor offset differential pressure valuefor a differential pressure sensor (e.g., air filter monitor 34). Whilea differential pressure sensor is used here as an example, it iscontemplated that sensor offsets from other types of sensors may beremoved in a similar manner. As discussed above, the air filter monitor34 may be in communication with the controller 18 via a wired orwireless communication link 42. In some cases, the controller 18 and/orprocessor 44 may be adapted to send a command to the HVAC system to turnoff the fan or blower 22 so that substantially no air is driven throughthe air filter 30 (Block 602). Once the fan or blower 22 has been turnedoff, air stops circulating through the ductwork (e.g., supply air duct10 and return air duct 14), and the system pressure may approach zero.Once the fan is “off” and the system pressure is at or near zero, thecontroller 18 and/or processor 44 may send a command to the air filtermonitor 34 to measure a sensor offset differential pressure valuebetween an upstream side of the air filter 30 and a downstream side ofthe air filter 30 (Block 604). The sensor offset differential pressurevalue may then be delivered to and stored within the memory 52 of thecontroller 18 (Block 608). In some cases, the controller may beconfigured to display the differential pressure measurement on thedisplay, but this is not required. The controller 18 may then return theHVAC system 4 to a previous or selected operating mode in which the fanis turned “on” so that air is driven through the air filter (Block 610).In some cases, the previous or selected operating mode or state may be acooling mode, a heating mode, a ventilation mode, a humidifying mode, adehumidifying mode, and the like.

The sensor offset differential pressure value obtained at or near zerosystem pressure may be indicative of the sensor offset. For example, ifthe sensor offset differential pressure value measured at or near zerosystem pressure is 0.1 w.c., then the sensor offset can be considered tobe equal to 0.1 w.c. The sensor offset differential pressure value maybe monitored by the controller 18 as a function of time and/or ambienttemperature. In some cases, when the sensor offset differential pressurevalue is obtained at or near zero system pressure, the controller 18 mayalso record the current ambient temperature and/or the amount of timelapsed from the last measurement of the sensor offset differentialpressure value. Other physical parameters such as absolute pressure orhumidity may also be monitored and recorded by the controller 18 as theymay also affect sensor offset and/or sensor drift. This information mayhelp the controller 18 to determine if the sensor offset differentialpressure value is still accurate using an algorithm designed for thispurpose. In some cases, the controller 18 may use the sensor offsetdifferential pressure value to determine whether or not the currentsensor offset differential pressure value calibration has expired. Insuch a case, the controller 18 may be configured to display a message tothe user on the controller display 62 that the sensor offsetdifferential pressure value calibration has expired and/or that a newsensor offset differential pressure value calibration may be necessary.

In some cases, the sensor offset differential pressure value may beobtained immediately or shortly after the initial system setup andcalibration. In other cases, the sensor offset differential pressurevalue may be obtained at any time during operation of the HVAC system,such as occasionally from time-to-time, at regularly scheduled intervalsaccording to an algorithm stored and executed by the controller 18,and/or in response to a user's request. In some cases, the sensor offsetdifferential pressure value may be obtained on a monthly basis, a weeklybasis, every five days, every three days, every 48 hours, every 24hours, every 12 hours, every 6 hours, every 20 hours of fan operation,whenever the temperature changes by more than 2 degrees, etc., asdesired.

In some cases, the controller 18 may be configured to operate the HVACsystem in a state in which substantially no air flows through the systemto generate a new sensor offset differential pressure value. The newsensor offset differential pressure value may replace a previouslyobtained sensor offset differential pressure value if the new valuediffers from the previously obtained value by a pre-determined amount.In other cases, the controller 18 may be configured to operate the HVACsystem in a state in which substantially no air flows through the systemto generate a new sensor offset differential pressure value if thetemperature or ambient pressure changes by more than a predeterminedthreshold amount. The new sensor offset differential pressure value maythen be stored in the memory of the controller. In certain cases, thecontroller may be configured to track the change in sensor offsetdifferential pressure values over time; thereby quantifying the sensoroffset drift. If the overall change in sensor offset differentialpressure values is greater than a predetermined threshold for apredetermined number of measurements, then the controller maybeconfigured to alert the user that an error has occurred.

In some cases, the sensor offset differential pressure value may be usedto more accurately calculate the differential pressure measurement usedto evaluate the filter status. Often, this measurement may be obtainedduring operation of HVAC system, as will be described in greater detailbelow. In some cases, for example, after the sensor offset differentialpressure value has been obtained; the controller 18 may send a commandto turn the fan or blower 22 of the HVAC system “on” so that air flow isdriven through the air filter. The controller 18 may then send a commandor otherwise instruct the air filter monitor 34 to sense a differentialpressure between the upstream side and the downstream side of the airfilter 30 to obtain an un-compensated differential pressure value (Block612). A compensated differential pressure measurement may be thenobtained by, for example, subtracting the sensor offset differentialpressure value (sensor offset) from the differential pressuremeasurement value according to the equation below (Block 614):

ΔPcompensated=ΔPmeasured−ΔPsensor offset

The compensated differential pressure measurement (ΔPcompensated) maythen be used, at least in part, to evaluate the status of the air filter30 (Block 616). For example, in some cases, the controller may beprogrammed with an algorithm that compares the compensated differentialpressure value to a predetermined air filter change threshold value todetermine a current status of the air filter. In other cases, thecontroller may be programmed with an algorithm that compares a firstcompensated differential pressure measurement to a second compensateddifferential pressure measurement to determine a current status of theair filter. The controller may then be configured to display the statusof the air filter to the user (Block 618).

In some cases, the controller 18 may be adapted to control the airfilter monitor 34 such that the air filter monitor may periodically oroccasionally monitor and measure the differential pressure across theair filter 30 during normal or routine operation of the HVAC system 4.The controller 18 and/or processor 44 may be programmed with analgorithm that uses this measurement to determine the status of the airfilter (e.g., clean or dirty), which may trigger a user alert or performany other suitable action, as desired.

FIG. 16 is a flow chart of an illustrative method 624 of monitoring astatus of an air filter of an HVAC system during routine or normaloperation of the HVAC system. In some cases, the status of the airfilter is monitored by comparing a differential pressure measurementobtained when the HVAC system is operating in a predetermined state suchas, for example, an air filter monitoring state. This method may beperiodically or occasionally repeated during routine or normal operationof the HVAC system, with each new differential pressure measurementused, at least in part, to determine and/or update the status of the airfilter. In some cases, the status of the air filter may be displayed bythe controller and/or may be used to trigger a user alert.

In some cases, the controller 18 and/or processor 44 may be adapted tocontrol the HVAC system equipment to place the HVAC system 4 in a an airfilter monitoring mode before commanding the air filter monitor 34 tomeasure, for example, the differential pressure across the air filter 30(Block 626). In some cases, the controller 18 and/or processor 44periodically command the air filter monitor 34 to measure thedifferential pressure (e.g. at regular scheduled intervals), fromtime-to-time, and/or “on demand” in response to a user request. In somecases, the controller 18 may be adapted to place the HVAC system in theair filter monitoring mode such that the air filter monitor may measurethe differential pressure across the air filter 30 on a monthly basis, aweekly basis, every five days, every three days, every 48 hours, every24 hours, every 12 hours, or every 6 hours, every 20 hours of fanoperation, or at any other suitable time, as desired. Alternatively, orin addition, the controller 18 may be programmed to place the HVACsystem in the air filter monitoring mode and to command or instruct theair filter monitor 34 to measure the differential pressure in responseto a user input or request (i.e., on demand).

In many cases, the same mode is used each time the air filter monitor 34is requested to measure the differential pressure across the air filter30. In some cases, the controller 18 may place the HVAC system in a “fanonly” mode prior to commanding the air filter monitor 34 to measure thedifferential pressure across the air filter 30. In a “fan only” mode,all HVAC system equipment except for the fan may be placed in the “offstate,” and for a zoned system, all dampers may be placed in the “open”position. In some cases, the heating or cooling element may be turned“off.” In other cases, the heating element and/or cooling element may beturned on. In any event, the controller 18 may be adapted to turn on thefan or blower 22. The fan or blower 22 may be operated at the same fanspeed each time a differential pressure measurement is made. Forvariable speed fans, the fan speed may be adjusted such that the fan isoperated at the highest fan speed available, but this is not required.What may be desirable is that the fan speed setting should be consistentfor each measurement, and all other variable (e.g. the on or off set ofthe heating and/or cooling element, the damper positions, etc., shouldalso be constant. Thus, it may provide a more consistent and accuratedifferential pressure measurement over time.

The differential pressure across the air filter may be measured whilethe HVAC system is operating in the air filter monitoring (e.g. “fanonly”) mode to obtain a differential pressure value or other value thatis related to the amount of air flow restriction presented by the airfilter (Block 628). The differential pressure value obtained while theHVAC system is operating in the air filter monitoring mode may be used,at least in part, to determine the current status of the air filter(Block 628).

The air filter monitor 34 may transmit or deliver data indicative of thedifferential pressure measurement to the controller 18, which may storethe data in the controller memory 52. The controller 18 may be adaptedto use this data to determine the status of the air filter 30. Asdiscussed above, the differential pressure measurement used to determinethe status of the air filter 30 may be compensated by subtracting asensor offset differential value from the measured differential pressurevalue to produce a compensated differential pressure value which may bemore accurate over time. In some cases, the controller 18 may beprogrammed with an algorithm that compares the differential pressurevalue from the air filter monitor 34 to an air filter change thresholdvalue determined by calibrating the filter monitor using either a cleanair filter or an at least partially blocked air filter (and/or blockingpanel), as described herein, to determine the current status of the airfilter, which may, in turn, be used to trigger a user alert.

After a differential pressure value associated with the HVAC systemoperating in the air filter monitoring has been obtained, the controller18 may operate the HVAC system in a different state other than the airfilter monitoring mode (Block 630). In this different operating state,at least one of the HVAC components may be operated in a different modethan it was while the HVAC system was operating in the air filtermonitoring mode. In some cases, the different operating state may be aprevious operating state of the HVAC system. For example, the controller18 may operate the HVAC system in a cooling mode, a heating mode, aventilation mode, a humidifying mode, a dehumidifying mode, and thelike. After a period of time, the controller may again place the HVACsystem in the air filter monitoring mode (Block 632). While the HVACsystem is operating in the air filter monitoring mode, the controllermay again command or request the air filter monitor 34 to obtain asecond or subsequent differential pressure measurement associated withthe air filter monitoring mode (Block 634). This second or subsequentvalue may be used, at least in part, to determine and/or update thestatus of the air filter after which, the controller may return the HVACsystem to a different operating state other than the air filtermonitoring mode. In some cases, the HVAC system may continue to operatein the different operating state according to a predetermined schedule.These steps may be occasionally repeated according to a predetermineschedule or in response to a user's request during the normal or routineoperation of the HVAC system.

As previously discussed, the differential pressure measurement (or othermeasure related to the amount of air flow restriction presented by theair filter) may be used to evaluate the status of the air filter 30. Insome cases, the controller 18 and/or processor 44 may be configured withan algorithm that compares the differential pressure measurement asmeasured by the air filter monitor 34 during operation of the HVACsystem 4 to the air filter change threshold value. This comparison maythen be used to determine the current status of the air filter.

In many cases, the controller 18 and/or processor 44 may be configuredto trigger a user alert when the value of a measured physical parameter(e.g. differential pressure value) falls outside of the limits set forthat particular parameter. In many cases, as discussed herein, thedifferential pressure across the air filter 30 may be monitored anddetected by the air filter monitor 34. The differential pressure valuethat is measured by the air filter monitor 34 during operation of theHVAC system is related to an amount of air flow restriction presented bythe air filter in the HVAC system. A dirty air filter will present moreof an air flow restriction than a clean filter. The controller 18 may beprogrammed to receive the measured differential pressure value from theair filter monitor and compare the measured differential pressure valueto the air filter change threshold value stored in the controllermemory. As described above, the air filter change threshold valueagainst which the measured differential pressure is evaluated may bedetermined using, for example, a clean air filter, an at least partiallyblocked air filter (and/or blocking panel) according to the methods asdescribed herein, or any other suitable method as desired. If thedifferential pressure measurement as measured by the air filter monitor34 during operation of the HVAC system 4 is greater than air filterchange threshold value then, in some cases, the controller 18 and/orprocessor 44 may display the status of the air filter 30 on the userinterface 48 (FIG. 2), provide an alarm, or perform any other suitableaction, as desired.

In some cases, the controller 18 may be configured to display any one ofa number of qualitative terms indicating the status of the air filter30. Exemplary qualitative terms that may be used to indicate the statusof the air filter include, but are not limited to, “CLEAN”, “GOOD”,“DIRTY”, “CHANGE FILTER SOON”, “REPLACE FILTER SOON” “CHANGE FILTERNEEDED”, “REPLACE FILTER NOW” and “FILTER CHANGE REQUIRED”, amongothers. In other cases, the controller 18 may be configured to display agraphical representation indicating the current status of the air filter30. For example, a maximum number of bars displayed on a graph mayrepresent that the air filter 30 is clean, while only a few barsdisplayed on a graph may indicate that a filter change is needed soon. Asingle bar or no bar at all displayed on a graph may represent that afilter change is needed. Additionally, color-coded labels or filterstatus indicators may be used to indicate if a filter change is needed.In some cases, the controller 18 may be configured to use a combinationof the various indicators, as described herein, to indicate the statusof the air filter 30. In still other cases, the controller 18 may beconfigured to sound an audible alert (e.g., intermittent beeps).

In some cases, the controller 18 may be configured to trigger a useralert depending upon the status of the air filter 30. In some cases, theuser alert may be a part of a three-level user alert system configuredto alert the user to the status of the air filter and, if necessary,alert the user to take action (i.e., change the filter, re-calibrate,check connections, calibration expired, etc.). The illustrativethree-level user alert system may, in some cases, combine qualitativeterms with a color code to alert the user to the filter status. In somecases, the three-level alert system may employ a stoplight metaphor. Forexample, when the differential pressure value across the air filterremains below the air filter change threshold value, the statusdisplayed by the controller may be labeled as “Good” and a green colormay be displayed. When the differential pressure value across the airfilter remains repeatedly at or above the air filter change thresholdvalue, sometimes for at least two or more consecutive measurements orfor a predetermined amount of time, the controller 18 may display alabel “Change Filter Soon”, along with the color yellow. In some cases,when the filter status changes from “Good” to “Change Filter Soon”, thecontroller 18 may initiate a timer that expires a predetermined amountof time later. The air filter monitor 34 may continue to monitor thedifferential pressure during this period, but this is not necessary. Thecontroller 18 may include a “snooze” function, which may permit the userto temporarily remove or delay the “Change Filter Soon” user alert for ashort period of time. If the user does not replace the filter duringthis snooze period, the controller may trigger a new user alert.

In some cases, once in the “Change Filter Soon” state, after apredetermined period of time set by the controller 18, the controller 18may change the filter status from “Change Filter Soon” to “Change FilterNow”, and may change the color from yellow to red. In some cases, the“snooze” function may no longer be available to the user.

FIGS. 17A-17E provide illustrative screens 652, 654, 656, 658, and 670that may be displayed by a controller (e.g., controller 18) configuredwith a three-level user alert system, as described above. FIGS. 17A,17B, and 17D provide illustrative home screens 652, 654, and 658, eachincluding a navigational bar 672, a first region 676, a second region680, and a third region 684. In some cases, the controller may beconfigured to display the air filter status 688 in the first region 676of the home screens 652, 654 and/or 658 as depicted in FIGS. 17A, 17B,and 17D. The air filter status 688 may be displayed in only a portion ofthe first region 676 or may be displayed such that it covers the entirefirst region 676 of the home screen 652, 652, and/or 658. Note, the airfilter status 688, when present, may replace the information that waspreviously displayed in the first region 676 of the home screen.

FIG. 17A shows an illustrative home screen 652 in which the filterstatus may be indicated as “Good.” In some cases, the qualitative termdisplayed on the screen may be color coded (e.g. green). In other cases,the first region 676, either in part or in whole, may be color coded(e.g. green, yellow, red) to indicate the status of the filter. Asindicated above, when the qualitative term indicates that the filterstatus is “Good”, the associated color code may be green.

FIG. 17B provides an illustrative home screen 654 that may be displayedwhen the controller determines that a filter change may be needed soon.A filter status indicator 688 indicative of the air filter status mayappear in the first region 676 of the home screen 654. As describedabove, when provided, one of many exemplary terms may be used toindicate the status of the air filter. In some cases, the air filterstatus indicator may display the term “Replace Air Filter Soon.”Additionally, the air filter status indicator 688 may be color coded.Here, the color associated with the filter status indicator 688 may beyellow. As shown in FIG. 17B, the air filter status may cover the entirefirst region 678 and may block other useful information such as, forexample, the current date and time from the user's view. This may annoythe user, prompting the user to take action more quickly than theyotherwise would if they could more easily ignore the user alert.

In some cases, the filter status indicator 688 may include a button,label, or tab 690 labeled “Press for more info.” In response to the userselecting the button 690 labeled “Press for more info”, the controllermay display a first user notification screen 656 as depicted in FIG.17C. The first user notification screen 656 may include a usernotification bar 692 which may include navigational arrows 694 a and 694b. The first user notification screen 656 may be configured to display auser notification or message 698 in a region 702 below the usernotification bar 692. Additional user notifications or messages (notshown) may be displayed by using the navigational arrows 694 a and 694 bprovided with the user notification bar 692. The user notification bar692 may also be configured to identify which message is displayed andhow many user notifications messages are available. For example, theuser notification bar 692 of FIG. 17C may indicate that the usernotification message that is displayed is the first of three availableuser notification messages.

The first user notification screen 656 additionally may include at leastone additional button for accessing more additional information oranother function of the controller. In some cases, the first usernotification screen 656 includes at least a delay button 706 which, whenselected, initiates a snooze function that may temporarily remove theuser alert displayed in the first region 676 of the home screen 654(FIG. 17B) for a predetermined period of time. The delay button 706 maybe labeled “Snooze”, “Remind me later”, “Delay”, “Dismiss”, and thelike. Additionally, the first user notification screen 656 may alsoinclude a button 708 labeled “View Filter Sizes” or “View Filter Info”that, when selected, may display the filter size, MERV rating(s), and orother information regarding the air filter. The first user notificationscreen 656 may also include at least one acknowledge button 710 that,when selected, may enable the user to acknowledge the user message 698displayed on the screen 656. Button 710 may be labeled “OK”,“Acknowledge”, “Done”, “Enter”, or any other suitable label as desired.Additionally, selecting button 710 may return the user to the previoushome screen such as, for example home screen 654 (FIG. 17B).

FIG. 17D provides an example of a home screen 658 that is displayed whenthe controller determines that a filter change is necessary now. Afilter status indicator 688 indicative of the air status may appear inthe first region 676 of the home screen 658. In this case, the airfilter status indicator 688 may display the term “Replace Air FilterNow”, “Filter Change Required”, or any other suitable label.Additionally, the air filter status indicator 688 may be color coded.Here, the color associated with the filter status indicator 688 may bered. As shown in FIG. 17D, the air filter indicator status 688 may coverthe entire first region 676 and may block other useful information suchas, for example, the current date and time from the user's view.

In some cases, the filter status indicator 688 may include a button,label, or tab 690 labeled “Press for more info.” In response to the userselecting the button 690 labeled “Press for more info”, the controllermay display a second user notification screen 670 as illustrated by FIG.17E. The second user notification screen 670 may be configured todisplay a user notification or message 714 that may indicate to the userthat the air filter needs to be changed. Additional information that maybe useful to the user may be included in the user notification message714. The second user notification screen 670 may also include at leastone additional button for accessing more additional information oranother function of the controller. In some cases, the second usernotification screen 670 includes at least a delay button 706 which, whenselected, initiates a snooze function and may temporarily remove theuser alert displayed in the first region 676 of the home screen 654(FIG. 17B). The delay button 706 may be labeled “Snooze”, “Remind melater”, “Delay”, “Dismiss”, and the like. In some cases, when thecontroller determines that a filter change is necessary now, the delaybutton 706 may be no longer available to the user for selection (e.g. itmay not be provided, grayed out, or otherwise not available forselection).

Like above, the second user notification screen 670 may also include abutton 708 labeled “View Filter Sizes” or “View Filter Info” that, whenselected, may display the filter size and/or MERV rating(s) of thefilter that may be used with the HVAC system and a button 709 that, whenselected, may display dealer information. The second user notificationscreen 670 may also include at least one acknowledge button 710 that,when selected, may enable the user to acknowledge the user message 714displayed on the screen 670. Button 710 may be labeled “OK”,“Acknowledge”, “Done”, or “Enter.” Additionally, selecting button 710may also return the user to the previous home screen such as, forexample, home screen 658 (FIG. 17D).

The user may replace the filter in response to a user alert displayed bythe controller. Upon replacement of the filter, the user may select abutton 718 labeled “New Filter Installed” or “Test New Filter” found onthe user notification screens 656 and 670 as illustrated in FIGS. 17Cand 17E. The user may access either of the user notification screens 656and 670 by selecting the button 690 labeled “Press for More Info” foundon the filter status indicator 688 or by selecting the appropriatebutton from the menu navigation bar 672 that is displayed on the homescreen 652, as illustrated in FIG. 17A.

In some cases, upon selection of button 718 labeled “New FilterInstalled,” the controller 18 may be configured to obtain a differentialpressure measurement to verify that in fact a clean filter has beeninstalled in the system. Additionally, the controller 18 may beconfigured to display a user alert if the differential pressuremeasurement obtained after a new filter has been installed is not belowthe air filter change threshold value. The differential pressuremeasurement obtained after a new filter has been installed may not bebelow the air filter change threshold value if a more restrictive filter(e.g., higher MERV rating) was installed, or if the user did notactually install a new and/or clean filter.

In some cases, the HVAC system 4 may be operating according to apredetermined schedule and/or mode in which the air filter monitor 34may periodically perform a new differential pressure measurement. Forexample, prior to the filter change, the HVAC system may be operating ina heating mode, a cooling mode, a ventilation mode, a humidifying mode,a dehumidifying mode, and the like. In other cases, the HVAC system maybe off. However, upon indication by the user that a new air filter hasbeen installed, the controller 18 may be configured to obtain a newdifferential pressure measurement shortly (within a few minutes) afterinstallation of the new air filter 30. This may provide relativelyimmediate feedback to the user regarding the installation of the newfilter.

FIG. 18 is a flow chart of a method 750 of evaluating a new air filter.In some cases, a user may install a new filter in the HVAC system. Insome cases, the controller 18 may accept an input from the userindicating that a new air filter has been installed (Block 752). Inresponse to the input, the controller 18 may be configured toautomatically operate the HVAC system 4 in an air filter verifying stateor mode before commanding the air filter monitor 34 to measure thedifferential pressure across the air filter 30 (Block 754). In manycases, prior to being operated in the air filter verifying state, atleast one of the HVAC components was operated in a different state. Insome cases, the controller 18 may operate the HVAC system in a “fanonly” mode in the air filter verifying state. In such a “fan only” mode,all HVAC system equipment other than the fan may be placed in the “offstate,” and for a zoned system, all dampers may be placed in the “open”position.

Once the HVAC system 4 is in the air filter verifying mode, thecontroller 18 may command the air filter monitor 34 to obtain adifferential pressure measurement across the air filter. Thedifferential pressure measurement that is obtained may be related to anamount of air flow restriction presented by the new air filter. The airfilter monitor 34 may transmit or deliver data indicative of thedifferential pressure measurement across the new air filter 30 to thecontroller 18. The controller 18 may receive the differential pressuremeasurement data from the air filter monitor and may store the datawithin the controller memory 52 (Block 756). The controller 18 and/orprocessor 44 may be adapted to use this data, at least in part, todetermine whether or not a proper new filter has been installed (Block758). In some cases, the differential pressure measurement used todetermine whether or not a proper new filter has been installed may beadjusted by subtracting a sensor offset value from the measureddifferential pressure to produce a compensated differential pressurevalue obtained with the new filter installed. In some cases, thecontroller 18 and/or processor 44 may be programmed with an algorithmthat compares the differential pressure measurement obtained using thenew filter to a predetermined threshold value to determine whether ornot a proper new air filter has been installed. In some instances, thepredetermined threshold value may be determined using a clean air filteror an at least partially blocked air filter (e.g. blocking panel)according to one of the methods, as described herein.

If the differential pressure measurement obtained using a new filter isless than the predetermined threshold value, the controller 18 mayautomatically return the HVAC system to its previous operating mode. Insome cases, the controller 18 may display a message to the userconfirming the installation of the new filter was successful, and maythen display a home screen (Block 760). If the differential pressuremeasurement obtained using the new filter is above the predeterminedthreshold value, the controller 18 may display an error message or otheruser alert. The user may then repeat the steps as outlined in Blocks752, 754, 756, and 758 using the same or a different filter. The usermay also access information about the appropriate filter(s) for the HVACsystem through the user interface, as described above. This informationmay be useful in determining if the correct type of filter for the HVACsystem has been installed. However, if the user simply re-installed thedirty filter, the controller may again display an error message or otheruser alert.

The HVAC system 4 may still continue to operate with a dirty filter;however, this may not provide adequate protection to the HVAC systemcomponents and may shorten their life expectancy. Regular replacement ofthe air filter may be recommended.

Having thus described several illustrative embodiments of the presentdisclosure, those of skill in the art will readily appreciate that yetother embodiments may be made and used within the scope of the claimshereto attached. Numerous advantages of the disclosure covered by thisdocument have been set forth in the foregoing description. It will beunderstood, however, that this disclosure is, in many respect, onlyillustrative. Changes may be made in details, particularly in matters ofshape, size, and arrangement of parts, without exceeding the scope ofthe disclosure. The disclosure's scope is, of course, defined in thelanguage in which the appended claims are expressed.

1. An HVAC controller for controlling an HVAC system, the HVAC systemhaving an air filter, the HVAC controller comprising: a controller; amemory coupled to the controller; a display coupled to the controller;wherein the controller is programmed to: receive a measured value thatis related to an amount of flow restriction presented by the air filterin the HVAC system; compare the received measured value to apre-determined threshold value stored in the memory; and implement athree-level user alert system in which the controller displays on thedisplay of the HVAC controller a first status indicator when thereceived measured value that is related to the amount of flowrestriction presented by the air filter in the HVAC system is less thanthe pre-determined threshold value, a second status indicator when themeasured value that is related to the amount of flow restrictionpresented by the air filter in the HVAC system is at least equal to thepre-determined threshold value but only for a predetermined amount oftime after the measured value is detected to be at least equal to thepre-determined threshold value, and a third status indicator after themeasured value that is related to the amount of flow restrictionpresented by the air filter in the HVAC system remains at least equal tothe pre-determined value for more than the predetermined amount of time.2. The HVAC controller of claim 1, wherein the first status indicatorcomprises a first qualitative term indicating that a status of the airfilter is good.
 3. The HVAC controller of claim 2, wherein the secondstatus indicator comprises a second qualitative term indicating that theair filter needs replacement soon.
 4. The HVAC controller of claim 3,wherein the third status indicator comprises a third qualitative termindicating that the air filter needs replacement.
 5. The HVAC controllerof claim 1, wherein the first status indicator comprises a first colorindicative of the status of the air filter.
 6. The HVAC controller ofclaim 5, wherein the second status indicator comprises a second colordifferent from the first color indicative of the status of the airfilter.
 7. The HVAC controller of claim 6, wherein the third statusindicator further comprises a third color different from the first colorand the second color indicative of the status of the air filter.
 8. TheHVAC controller of claim 1, wherein the three-level user alert systemincludes a stop-light metaphor, where the first status indicatordisplays a green color, the second status indicator displays a yellowcolor, and the third status indicator displays a red color.
 9. The HVACcontroller of claim 1, wherein when the measured value is at least equalto the pre-determined value for at least two consecutive measurements,the controller is configured to implement a timer for a pre-determinedperiod of time after which the controller is configured to update thecontroller display to display the third status indicator.
 10. The HVACcontroller of claim 1, wherein the received measure value that isrelated to the amount of flow restriction presented by the air filter inthe HVAC system is a measured differential pressure value taken acrossthe air filter.
 11. The HVAC controller of claim 1, wherein the receivedmeasure value that is related to the amount of flow restrictionpresented by the air filter in the HVAC system is a measured air flowrate representative of air flowing through the air filter.
 12. An HVACcontroller for controlling an HVAC system, the HVAC system having an airfilter, the HVAC controller comprising: a controller; a memory coupledto the controller; a display coupled to the controller; wherein thecontroller is programmed to: receive a measure that is related to anamount of flow restriction presented by the air filter in the HVACsystem; using the measure that is related to the amount of flowrestriction presented by the air filter in the HVAC system to determinewhether the air filter does not need replacing, the air filter needs tobe replaced soon, or the air filter should be replaced now; and displayon the display of the HVAC controller an air filter status indicator,wherein the air filter status indicator includes a stop-light metaphor,where the air filter status indicator displays a green color when theair filter does not need replacing, displays a yellow color when the airfilter needs to be replaced soon, and displays a red color when the airfilter should be replaced now.
 13. The HVAC controller of claim 12,wherein air filter status indicator further includes displaying aqualitative term indicative of the current status of the air filter. 14.The HVAC controller of claim 12, wherein the controller determines thatthe air filter does not need replacing when the measure that is relatedto the amount of flow restriction presented by the air filter in theHVAC system is below a threshold value.
 15. The HVAC controller of claim14, wherein the controller determines that the air filter needsreplacing soon when the measure that is related to the amount of flowrestriction presented by the air filter in the HVAC system has been ator above the threshold value for less than a predetermined amount oftime.
 16. The HVAC controller of claim 15, wherein the controllerdetermines that the air filter should be replaced now when the measurethat is related to the amount of flow restriction presented by the airfilter in the HVAC system has been at or above the threshold value formore than the predetermined amount of time.
 17. A method of indicating astatus of an air filter on an HVAC controller that includes a display,the method comprising: receiving a measure that is related to an amountof flow restriction presented by an air filter in an HVAC system; usingthe measure that is related to the amount of flow restriction presentedby the air filter in the HVAC system to determine whether the air filterdoes not need replacing, the air filter needs to be replaced soon, orthe air filter should be replaced now; and displaying on the display ofthe HVAC controller an air filter status indicator, wherein the airfilter status indicator includes a stop-light metaphor, where the airfilter status indicator displays a green color when the air filter doesnot need replacing, displays a yellow color when the air filter needs tobe replaced soon, and displays a red color when the air filter should bereplaced now.
 18. The method of claim 17, wherein determining stepdetermines that the air filter does not need replacing when the measurethat is related to the amount of flow restriction presented by the airfilter in the HVAC system is below a threshold value.
 19. The method ofclaim 18, wherein the determining step determines that the air filterneeds replacing soon when the measure that is related to the amount offlow restriction presented by the air filter in the HVAC system has beenat or above the threshold value for less than a predetermined amount oftime.
 20. The method of claim 15, wherein the determining stepdetermines that the air filter should be replaced now when the measurethat is related to the amount of flow restriction presented by the airfilter in the HVAC system has been at or above the threshold value formore than the predetermined amount of time.